- Classification: Lightning Rod
- Material: Stainless Steel
- Working Voltage: High Voltage
- Certification: ISO9001, CE
- main material is stainless steel, acid-proof and rust-proof.
- Strong Wind bearing ability.
- Rod part is made from special material, with stronger air termination withstand capacity.
- Special design, with decorative function for buildings.
- Simple construction, convenient installation.
Lightning rods protection zone should be calculated according to standard stipulated rolling sphere method. If the lightning conductor does not meet the requirement, it can adopt special rail or tower to increase the height; If the protection area is wide, it can consider to using several lightning conductors to cover protection area.
Installation of lightning rods:
Firstly, install the assembled lightning rod on the top of the building (fixed the lightning rod with the building by the four 10mm hold of the flange, please refer to the drawing of flange). Using Zinc bonded flat steel 40mm× 4mm or round steel 12mm as down conductor, which should be welded to the flange from grounding electrode by means of direct road. The down conductor should be attaching to the building (the outer side of the wall), and be fixed to the wall of interval 1.5m. In the end, the welded part should be painted by rust-proof material.
|Operating temperature||-40~+80 degree|
|Relative humidity||≤ 95%|
|Diameter of Decorative ball (D)||φ 200(mm)|
|Max. Diameter of the rod (M)||φ 38(mm)|
|Diameter of Flange (T)||φ 240(mm)|
|Thickness of Flange||8(mm)|
|Fixup orifice of Flange||φ 10(mm)x 4|
|Housing material||Stainless steel(202)|
|Max. impulse current Iimp||300 kA|
|No. of main rod||1|